Please use this identifier to cite or link to this item:
Full metadata record
|dc.description.abstract||This paper presents a substation grounding grid analysis with the variation of soil layer depth. The grounding grid system of a practical 22 kV substation, in which the ground grid is made from copper, is calculated by virtue of the CDEGS software. The study, supported by Provincial Electricity Authority (PEA), Thailand, is based on grounding grid system of Royal Flora RATCHAPHRUEK substation. The supporting soil resistivity data has been obtained from field tests at the substationThe result shows that soil resistivity was interpreted to two-layer soil structure with low resistivity top layer and high resistivity bottom layer. The studied ground grid system is installed with constant 3m ground rods. When the ground layer depth of the grid is increased, it directly affects to reduce the value of Ground Potential Rise (GPR). On the other hand, with the same grid configuration buried in the high resistivities bottom layer, its GPR is not reduced, that is, the more layer depth of high resistivities bottom layer, the more value of GPR. In addition, the grid with the different ground rods length also gives the different results. GPR is continuously reduced when the rod length is lengthened even though the bottom layer resistivity is higher than the top layer. ©2007 IEEE.||en_US|
|dc.title||Ground layer depth and the effect of GPR||en_US|
|article.title.sourcetitle||IEEE PES PowerAfrica 2007 Conference and Exposition, PowerAfrica||en_US|
|article.stream.affiliations||Chiang Mai University||en_US|
|Appears in Collections:||CMUL: Journal Articles|
Files in This Item:
There are no files associated with this item.
Items in CMUIR are protected by copyright, with all rights reserved, unless otherwise indicated.