Please use this identifier to cite or link to this item:
|Title:||Analysis of replacement from disconnecting switch to circuit breaker for 500 kV line shunt reactor|
|Abstract:||© 2018 IEEE. In energize and de-energize shunt reactor, through the circuit breaker will result in overcurrent and overvoltage, which will impact on equipment and power quality in the transmission network. This paper will perform an analysis of the energize and de-energize shunt reactors. By switching shunt reactors, the three poles trip circuit breaker will cause an inductive current during interruption by the system model to simulate the transient induction during switching with the PSCAD/EMTDC program. EGAT's 500 kV transmission line is a case study for analyzing overcurrent, current chopping, chopping overvoltage and re- ignition phenomena caused by switching circuit breaker.|
|Appears in Collections:||CMUL: Journal Articles|
Files in This Item:
There are no files associated with this item.
Items in CMUIR are protected by copyright, with all rights reserved, unless otherwise indicated.